Major factors contributing to a rapid spread of fire at the Sofa Super Store in Charleston, S.C., on June 18, 2007, included large open spaces with furniture providing high fuel loads, the inward rush of air following the breaking of windows, and a lack of sprinklers, according to a draft report released October 28, 2010, for public comment by the National Institute of Standards and Technology (NIST). The fire trapped and killed nine firefighters, the most firefighter fatalities in a single event since 9/11.
On the basis of its findings, the NIST technical study team made 11 recommendations for enhancing building, occupant and firefighter safety nationwide. The team urged states and local communities to adopt current national model building and fire safety codes. 1 If today's model codes had been in place and rigorously followed in Charleston in 2007, the study authors said, the conditions that led to the rapid fire spread in the Sofa Super Store probably would have been prevented.
"Furniture stores typically have large amounts of combustible material and represent a significant fire hazard," said NIST study leader Nelson Bryner. "Model building codes should require both new and existing furniture stores to have automatic sprinklers, especially if those stores include large, open display areas."
Specifically, the NIST report calls for national model building and fire codes to require sprinklers for all new commercial retail furniture stores regardless of size, and for existing retail furniture stores with any single display area of greater than 190 square meters (2,000 square feet). Other recommendations include adopting model codes that cover high fuel load situations (such as a furniture store), ensuring proper fire inspections and building plan examinations, and encouraging research for a better understanding of fire situations such as venting of smoke from burning buildings and the spread of fire on furniture.
NIST welcomes comments on the draft report and its recommendations. To be considered for the final report, comments must be received by noon EST on Dec. 2, 2010. Comments may be submitted via e-mail to email@example.com; fax to (301) 975-4052; or mail to the attention of NIST Technical Study: Sofa Super Store, NIST, 100 Bureau Dr., Stop 8660, Gaithersburg, MD 20899-8660.
Once the final report is published, NIST will work with the appropriate committees of the International Code Council (ICC) on using the study's recommendations to improve provisions in model building and fire codes. NIST also will work with the major organizations representing state and local governments—including building and fire officials—and firefighters to encourage them to consider its recommendations.
To read the full press release and to access the draft study report and supplementary materials, go here.
1The International Code Council (ICC) I-Codes are used as models for building and fire regulations promulgated and enforced by U.S. state and local jurisdictions. Those jurisdictions have the option of incorporating some or all of the code's provisions but generally adopt most provisions.