Combined Buoyancy- and Pressure-Driven Flow Through a Horizontal Vent.
Leonard Y. Cooper
Combined buoyancy- and pressure-driven (i.e., forced) flow through a horizontal vent is considered where the vent-connected spaces near the elevation of the vent are filled with fluids of different density in an unstable configuration, with the density of the top space larger than that of the bottom space. With zero-to-moderate cross-vent pressure difference the instability leads to a bi-directional exchange flow between the two spaces. For relatively large cross-vent pressure difference the flow through the vent is unidirectional, from the high- to the low-pressure space. An anomaly of a standard vent flow model, which uses cross-vent pressure difference to predict stable unidirectional flow according to Bernoulli's equation (i.e., flow-rate is proportional to [equation], where [equation] is an orifice coefficient), is discussed. Such a model does not predict the expected bi-directional flow at small to moderate [equation] or non-zero flow at [equation]. Even when cross-vent pressure difference exceeds the critical value which defines the onset of unidirectional or "flooding" flow, it has been determined experimentally that until cross-vent pressure difference exceeds many times [equation] there is a significant dependence of [equation] on the relative buoyancy of the upper and lower fluids. Also, it has been shown theoretically that the location of the high-pressure side of the vent, i.e., the top or bottom, can be expected to influence vent flow characteristics. Previously published experimental data and results of an analysis of the relevant boundary value problems are used to develop a flow model which takes all of these effects into account. The result is a uniformly valid algorithm to calculate flow through shallow (small depth-to-span ratio), horizontal, circular vents under the high-Grashof number conditions. This is suitable for general use in zone-type compartment fire models (e.g., an ambient temperature environment above the vent and a hot smoky environ
vents, building fires, compartment fires, computer models, fire models, mathematical models, zone models, ceiling vents, oxygen concentration
Combined Buoyancy- and Pressure-Driven Flow Through a Horizontal Vent., NIST Interagency/Internal Report (NISTIR), National Institute of Standards and Technology, Gaithersburg, MD, [online], https://doi.org/10.6028/NIST.IR.5384
(Accessed May 31, 2023)