Take a sneak peek at the new NIST.gov and let us know what you think!
(Please note: some content may not be complete on the beta site.).
NIST Authors in Bold
|Author(s):||John L. Gross;|
|Title:||Fire Endurance Testing of Floor Systems Effects of Scale and Restraint|
|Abstract:||Three standard fire resistance tests (ASTM E 119) were conducted on a composite floor system to study the effects of 1) test restraint conditions, and 2) scale of the test. Two full-scale tests, 35 ft (10.7 m) span, and one half-scale test, 17 ft (5.2 m) span, were conducted. Two tests were conducted under restrained conditions and one under unrestrained conditions. Results showed that the full-scale restrained floor system obtained a fire resistance rating of 1 h, while the full-scale unrestrained floor system achieved a 2 h rating. Past experience with the ASTM E119 test method would lead one to expect that the unrestrained floor assembly would not perform as well as the restrained assembly, and therefore, would receive a lower fire rating. For the full- and half-scale floor systems tested in the restrained condition, the full-scale specimen obtained a fire resistance rating of 1 h, while the half-scale specimen achieved a 2 h rating. Both tests would be expected to produce the same fire resistance rating.|
|Citation:||Special Publication (NIST SP) - 1054|
|Keywords:||ASTM E119,fire,fire resistamce,fire testomg,floor systems,standard fire resistance tests,testing|
|Research Areas:||Building and Fire Research|