Take a sneak peek at the new NIST.gov and let us know what you think!
(Please note: some content may not be complete on the beta site.).
NIST Authors in Bold
|Author(s):||Thomas G. Cleary; Jiann C. Yang;|
|Title:||Prediction of Light Scattering and Ionization Chamber Sensor Response to Smolder Smoke Aerosols|
|Published:||September 08, 2009|
|Abstract:||Diagnostic equipment developed for an International Space Station experiment, the Smoke Aerosol Measurement Experiment (SAME), utilized three measurement devices to determine size properties of the smoke aerosols generated. They consisted of a light-scattering photometer, an ionization chamber from a residential smoke alarm, and a condensation particle counter. The ability to predict the ionization chamber and photometer outputs from aerosol size distribution and concentration information was examined. Using dioctyl phthalate aerosols ranging in mean size from about 0.1 m to 1.0 m, the relative expanded uncertainty of the ionization chamber prediction using total aerosol length was + 12 %, while the relative expanded uncertainty of the photometer prediction was + 33 % using a Mie-scattering model and the aerosol number concentration, size distribution, and refractive index. Smoke was generated from electrically heated silicone, Kapton, Teflon, cotton wick, and dibutyl phthalate samples using the SAME experimental hardware. The smokes were measured with the SAME diagnostic equipment plus additional aerosol instrumentation. Using measured size distributions and particle number concentrations along with estimates of the refractive index, the photometer predictions were within + 25 % for most smokes except Kapton which appears to have an agglomerate structure as determined by electron microscopy.|
|Proceedings:||14th International Conference on Automatic Fire Detection "AUBE '09"|
|Dates:||September 9-11, 2009|
|Keywords:||smoke detection, size distribution, light scattering|
|Research Areas:||Fire Detection|
|PDF version:||Click here to retrieve PDF version of paper (117KB)|